Radon Mitigation Systems
Radon mitigation is any process or system used to reduce radon concentrations in the breathing zones of occupied buildings. The goal of a radon mitigation system is to reduce the indoor radon levels to below the EPA action level of 4 pCi/L. A quality radon reduction (mitigation) system is often able to reduce the annual average radon level to below 2 pCi/L. In general, costs can range from approximately $800-$2500, with the average reduction system costing approximately $1500.
Financial Assistance for Installing Radon Mitigation SystemsThe Minnesota Housing Finance Agency (MHFA) offers a financing program, The Fix-Up Fund, for homeowners looking to make improvements on the their homes. Fix-Up Fund financing can make radon mitigation more affordable for eligible homeowners through low-interest fixed rate loans. If a mitigation system does not meet the minimum loan requirement, it can easily be paired with other home improvements to further increase the affordability of your projects. For more information visit the MHFA fix-up fund website.
Any home can have a radon problem, no matter what type of foundation it has.
- Basement: provides a large surface area in contact with soil material. Radon can enter through cracks in the concrete, or through floor-to-wall joints or control joints. Since many Minnesota homes use their basements as living space, exposure to radon can be further increased. But radon can enter a home regardless of whether or not there is a basement.
- Slab-On-Grade: Slabs built on grade can have many openings that allow radon to enter, just as in a basement.
- Crawl Space: Homes with crawl spaces can also have elevated radon levels. The vacuum effect can draw radon gas from a crawl space into the home.
- Manufactured Homes: Unless these buildings are placed on supports without skirting around them, interior air pressure vacuums can cause radon to enter manufactured homes, as well.
The are four types of soil suction systems: sub-slab, drain tile, sub-membrane and block wall.
10 Step Process
- Homeowner's radon test reveals the home has a radon problem.
- Homeowner contacts certified mitigators to request bids.
- Contractor does a walk-through of the home to identify problems then outlines the mitigation system they recommend.
- Homeowner reviews key questions with each contractor requesting a proposal bid and references.
- Homeowner evaluates and compares contractor recommendations, bids and contracts, selecting the contractor and scheduling the work.
- Contractor may perform diagnostic testing to ensure proper size and installation methods are applied.
- Contractor seals required areas, e.g., large cracks, crawl spaces, sumps, etc.
- Contractor installs the mitigation system, i.e., suction pit or ventilation, pipe routing, etc. Electrical hook-up completed by licensed electrician, not a licensed contractor.
- Contractor provides full explanation of system's operation to homeowner.
- Homeowner or contractor test the home to ensure the system is reducing radon to the desired level.
Other methods to Reduce radon levels
Other radon reduction techniques may be considered to reduce the radon gas levels that are circulating within the home. Many of these methods are used only as temporary measures, or in combination with other measures, like the ventilation or suction system.
- Ventilation: can sometimes lower indoor radon levels in crawl spaces by reducing the home's suction on the soil and by diluting the radon beneath the house. Passive ventilation is achieved by opening or installing vents. Active ventilation uses a fan to blow air through the crawl space. To be effective, ventilation is often used with sub-membrane depressurization, which covers the dirt of the crawl space floor with a plastic sheet. A pipe then draws the radon air from under the sheet to the outside.
- Sealing: cracks and openings in the foundation is a basic step in radon mitigation. Sealing will limit the flow of radon, making other mitigation techniques more efficient. This is a temporary measure because normal settling of a home opens new entry routes and reopens old ones.
- Pressurization: uses a fan to blow air into the lower level of the home, creating enough pressure to prevent radon entering. To maintain enough pressure, doors and windows at the lowest level must not be left open.
- Heat recovery ventilator (HRV): (also called an air-to-air heat exchanger) is used to increase ventilation in all or part of a home. The HRV introduces outdoor air by using the heated or cooled exhausted air to warm or cool the incoming air.
What to look for in an installed system
- Radon reduction systems must be clearly labeled. This will avoid accidental changes to the system which could disrupt its function.
- The exhaust pipe(s) of soil suction systems must vent above the surface of the roof and 10 feet or more above the ground, and at least 10 feet away from windows, doors, or other openings that could allow the radon to reenter the house, if the exhaust pipe(s) do not vent at least 2 feet above these openings.
- The exhaust fan must not be located in or below a livable area. For instance, it should be in an unoccupied attic of the house or outside — not in a basement!
- A warning device must be installed to alert you if an active system stops working properly.
- A post-mitigation radon test should be done no sooner than 24 hours after your system is in operation with the fan on, and last at least 48 hours.
- Attached written operating and maintenance instructions and copies of any warranties.
Final note: Be aware of uncertified installers and super cheap mitigation rates (less than $1,000). Only radon professionals on the MDH list should be hired to do radon mitigation. Price quotes promising really low installation rates are often too good to be true and leave the consumer holding the bag. Be sure to get a firm price and avoid hidden fees for future work when it may become necessary. Also, do not pay for the system in full before the work is complete. A valid radon test showing reduced levels should be obtained prior to full payment.